Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
For security reasons, the communication supply (at the front plate) of Sepam 1000+ is totally isolated from the product internal power supply.
The communication supply is done by the PC serial port.
In some cases, when the serial port power supply is weak, and due to the components tolerances, a communication failure could occur.
If this kind of failure occurs again, it is advisable to use another PC.
Improvement of the communication level efficiency is available with the new Sepam base board (universal power supply from 24 to 250V).
This problem does not concern Sepam 1000+ series 40
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 1000+ (Sepam Series 20)
All content © 1992-2008 Schneider Electric