Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Voltage variations of the power supply that are out of allowable range, due to inrush currents and other influences (originating from sources other than the Sepam units) can provoke multiple and successive power cycles (starts/stops) of the Sepam device. This can induce finally the thermal failure of the internal protective fuse.
Effectively Sepam energizing provokes inrush current which overheats the fuse. Multiple and successive starts/stops of Sepam avoid do not allow the proper cooling of the fuse and lead it to burn out.
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 1000+ (Sepam Series 20 and Sepam Series 40)
All content © 1992-2008 Schneider Electric