Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Is there an extra contact available on melting alloy overloads for the Mflex and Eflex drives?
M-Flex and E-Flex
Dry contact on OLR
The overload has 1 N.O and 1 N.C. contacts. No other contacts can be added to the overload. The 95, 96 N.C. contact of the overload is used to open the isolation or bypass contactors, if the overload trips. The 98, 97 N.O. contact isn't used but it could be used for overload trip indication.