Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Is there an extra contact available on melting alloy overloads for the Mflex and Eflex drives?
M-Flex and E-Flex
Dry contact on OLR
The overload has 1 N.O and 1 N.C. contacts. No other contacts can be added to the overload. The 95, 96 N.C. contact of the overload is used to open the isolation or bypass contactors, if the overload trips. The 98, 97 N.O. contact isn't used but it could be used for overload trip indication.