Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The ATV61 drive with a DeviceNet option card on will not start via the network commands.
All ATV61 with optional VW3A3309 DeviceNet option cards.
Drive will not start using network commands with DeviceNet option card installed on the drive.
Check the reference and command channel make sure its set for communications card control.
The PLC (Logix 5000) could read data but was not able to write. Verified that I/O Scanner was set up properly but he scanner module was Idle.
Restarted scanner module.
Now we find out the CMD and LFRD are DINT (32 bit words). The 1st 16 bits of the word are the CMD and the 2nd 16 bits are for the LFRD speed reference.
He needs to write to the 32 bit word accordingly for start/stop and speed reference.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!