Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The secondary fuse of the control transformer is blowing.
S-Flex 21, S-Flex 212, E-Flex, M-Flex
All models and serial numbers
Caused by short circuit to ground. Possible loose wire or defective or damaged contactor coil.
Trace short circuit with ohm meter. Replace coil if necessary.