The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
What are possible causes for over braking faults OBF in the ATV61 or ATV71 drives?
Braking too sudden or driving load
If the drive trips while running, monitor for voltage surges and spikes, you may need to install a line reactor or a surge suppressor.
If the drive is tripping while decelerating, increase deceleration time. You may need to add a Dynamic Braking resistor.
If the drive trips on a Start command, check to see that the Catch on the Fly parameter is enabled in the Fault Management menu (if application allows). Also verify wiring between drive and motor as well as motor connections.
For ATV71 applications with off center loads (Jack pump, shaker table, vibratory feeder) it would be worthwhile testing the ENA System set to YES (Menu 1.4 [Motor Control]). Note that the Motor control type must be set to SVC V.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!