Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Issue: ATV61 or ATV71 AC drive display motor short circuit or IGBT short circuit fault codes when powered by a generator
Product Line: Altivar ATV61 and ATV71
Environment: All ATV61 and ATV71's when powered with a generator
Cause: These are not true short circuit faults but are occurring as a result of power supply instability and high voltage during the transient state of initial generator power.
Resolution: Investigate and correct the instability and over voltage conditions during transient state of initial generator power.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!