Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Issue: ATV61 or ATV71 AC drive display motor short circuit or IGBT short circuit fault codes when powered by a generator
Product Line: Altivar ATV61 and ATV71
Environment: All ATV61 and ATV71's when powered with a generator
Cause: These are not true short circuit faults but are occurring as a result of power supply instability and high voltage during the transient state of initial generator power.
Resolution: Investigate and correct the instability and over voltage conditions during transient state of initial generator power.