Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Can multiple motor leads be wired in the same conduit?
Multiple motor and or Line leads from different drives in the same conduit.
It is not recommended to run the motor leads from different drives in the same conduit.
Multiple motor leads from different drives is not recommended because the noise generated from the pulse width modulated (PWM) waveform can cause cross-talk resulting in possible nuisance tripping.